QuietTiger LSU Fan New Orleans Member since Dec 2003 20397 posts Online
re: why the hell won't my AC work? fixed, thanks(Posted by QuietTiger on 7/25/13 at 7:05 pm to TH03)
quote: but it won't stay on if I let go
It's not getting called from the furnace. Did you try to spin the squirrel cage? Remember to have the thermo in ON position and depress any deadman switch at the door of the unit. Good luck, I have to go lower my thermo and cook some dinner.
re: why the hell won't my AC work? fixed, thanks(Posted by wartiger2004 on 7/25/13 at 7:20 pm to TH03)
Ok make sure the door is on tightly so the door switch makes contact.also do you have a digital t stat or regular if digital does it have batteries as a backup.It sounds like you're not getting 24 volts to your tstat
re: why the hell won't my AC work? fixed, thanks(Posted by NWLATigerfan on 7/25/13 at 7:35 pm to TH03)
A/C Guy here. let me try to offer some help. You have lost power to control transformer on indoor unit. this could be the result of many things. lets start with is this a gas furnace or electric heat and or heat pump?